UF / UP / U6 fault code
As the largest independant Mitsubishi Electric service and repair company in Adelaide South Australia we see a lot of Mitsi units. A common fault we see on Mitsubishi Electric ducted systems is the UF, UP or U6 error code. This fault code commonly represents a fault within the Outdoor Power PCB, Compressor electrical circuit or Compressor bearings. Of these 3 similar errors codes, the most common to see is the U6, UP or UF. This will be displayed on your wall controller after the unit tries to run 10 times in a row without success.
Mitsubishi Electric define UF / U6 / UP faults as follows
- UF - Compressor overcurrent interruption (when compressor locked). Abnormal if overcurrent of DC bus or compressor is detected within 30 seconds after compressor starts operating.
- U6 - Power module abnormal. Check abnormality by driving power module in case overcurrent is detected. (UF or UP error condition).
- UP - Compressor overcurrent interruption. Abnormal if overcurrent DC bus or compressor is detected after compressor starts operating for 30 seconds.
Common issues that can cause U6 / UF / UP faults
- Failure or the Power PCB in outdoor unit
- Electrical failure or fusion of Compressor
- Seized bearings in the Compressor
- Disconnected/broken wiring to the compressor
- Closed service valves at outdoor unit
- Low voltage at outdoor unit
Tests to determine faulty components
Testing your Mitsubishi Electric air conditioner to determine the cause of a U6, UF or UP fault is relatively straight forward if you know what to look for. Below is the main checks to determine what component has caused this fault. These test are not DIY and will require a Mitsubishi Electric specialist to test correctly.
Disclaimer - Electricity is dangerous and can kill you. The following information is for educational purposes only. Tests must be performed by an authorised service provider or Mitsubishi Electric specialist. Do not try this to perform these test without the proper expertise and qualifications.
- Check for correct voltage at the outdoor unit, 240v or 415v
- If power feed is incorrect, contact a licensed electrician or SA Power Networks to rectify power supply to unit/property
- Check both outdoor service valves are fully open
- If valves are shut, open valves
- Check for visual damage to the Outdoor Power PCB. This could include lizard or rodent damage
- If damage is found replace Power PCB then further test unit operation
- Check for visual damage to the wiring between the Power PCB and the compressor. This could include lizard or rodent damage
- If damage is found, replace damaged cable
- Check for correct DC voltage to the compressor is equal and correct
- If DC voltage is incorrect, replace Power PCB
- Check for equal voltage output from the Power PCB diodes using an inverter checker
- If inverter checker LED’s are unequal, replace Power PCB
- If the voltage and diodes have tested correctly and no visual damage is found, it is likely the compressor bearings have seized
- The compressor will need to be replaced and the unit further tested
Costs involved to repair your Mitsubishi Electric air conditioning system
It is important to ensure the correct tests are completed to determine what part requires replacement. It’s an expensive exercise to replace a compressor when only a damaged wire or PCB is to blame. The cost to replace the Power PCB can range from $800.00 - $1,300 depending on the model of your Mitsubishi Electric unit. Compressor replacement cost can vary from $2,500 - $4,000 depending on the model of your Mitsubishi Electric unit. The amount of refrigerant, outdoor unit location, access and labour involved to replace the compressor will also contribute to higher costs. Ensuring the correct parts are diagnosed is vital to make certain you do not waste money on unnecessary parts.
In a nutshell
- UF/U6/UF faults can be caused by similar problems
- Correctly determining the faulty part can save you $1,000’s
- Using a Mitsubishi Electric specialist will ensure the problem is correctly diagnosed and repaired
T&K Airpower have been working to keep Adelaide homes comfortable for the last 20 years. We specialise in Temperzone, Hitachi and Mitsubishi Electric air conditioning units and know how they tick. Do you have a U6, UF or UP fault displayed on your Mitsubishi Electric air conditioning unit? Give us a call and we will be more than happy to help.
Call 08 8296 7888 to Book A Service Today
Or complete the form below and one of our friendly staff will call you within 24 hours.
We have just had our air conditioner serviced and some parts replaced by Sean and Abbey. Their level of service was outstanding. They were efficient, friendly, professional and cleaned up after themselves! THANKS.
“Excellent service from everybody in the T&K team. I would highly recommend them - they always go above and beyond!”
"Great all round professionals .They supplied and installed my split a/c at a very reasonable price. Highly recommend."
Tea Tree Gully, SA
"Awesome service from a really excellent and friendly team."
Banksia Park, SA
We chose T&K Airpower as Oliver was prompt and informative in the selection of our replacement aircon system, and the installation was done professionally and works very well. On time and no hesitation to correct a small follow up issue that arose, but was quickly resolved by Marty.
Rose Park, SA
After contacting your office enquiring about a warranty on our air conditioners remote control yesterday morning 26/3/2018 at approx 10.30 am, we were advised of an 1800 number and the response was amazing. We recieved an sms yesterday afternoon advising us that a new remote was on its way and we recieved it in this mornings post 27/3/2018. WE RATE THIS COMPANY A 5 STAR RATING IN REGARDS TO CUSTOMER SERVICE. THANK YOU TO ALL CONCERNED.
Adelaide, South Australia
"I called to say we were absolutely thrilled with Marty's work he fixed our air conditioner and its working perfectly... It's an older unit, a Bradway and we didn't want to spend anymore money he tried a few things as the unit was only working 75% and whatever was done as a part of the service worked a treat we couldn't be happier.... Please thank him and pass on our feed back we really want him to know what a great job he's done and how very happy we are!!!"
I'm writing to thank you and T&K (especially Brett and Sam) for their efforts to restore my air conditioning. The new fan motor is now purring away, and I'm astonished to find that it is almost silent. I appreciate the comprehensive and high-quality service provided by T&K.
Rose Park, SA
“These guys fix the problems the others can't even diagnose. True professionals.”
Please pass on our thanks to your technician (Sean) for the first class work he did for us. He was thorough and clear with his advice for the ongoing care of the unit, pleasant and efficient.