Mitsubishi Electric outdoor unit noisy - Outdoor Fan Bracket issues
If you own a Mitsubishi Electric ducted air conditioning unit, you may one day hear a knocking sound from your outdoor unit. If this happens, check the outdoor unit fans to see if they are wobbling excessively back and forward. A common area of failure, especially with systems located near salt water, is the outdoor fan motor bracket. These brackets either rust out at the base, or the rubber mounts disintegrate at the top. Either way, this can cause the fan motor/s to drop forward and catch on the fan housing or wobble back and forth. Best case, this noise is loud and annoying, worst case the fan motor can jam against the fan housing and trip the unit out on fault or damage the fan motor and blade. Preliminary symptoms can often be picked up during a preventative maintenance service if the technician knows what to look for.
Replacing the fan motor bracket is the easiest way to stop this problem. Genuine Mitsubishi Electric fan motor brackets typically cost around the $300-$400 mark supply and installed by a professional service technician. This could be done DIY but not recommended as the motor/s have to be removed in order to install the new bracket. Contact Mitsubishi Electric on 1300 292 732 to find your local service specialist.
New fan motor bracket installed
In a nutshell
Simple and cheap repair if found early
Can be detrimental if left unfixed
Should be completed by a professional service technician
T&K Airpower have been working to keep Adelaide homes comfortable for over 20 years. We specialise in Temperzone, Hitachi and Mitsubishi Electric air conditioning units and know how they tick. Strange noises coming from your Mitsubishi Electric unit? Give us a call and we will be more than happy to help.
Call 08 8296 7888 or 07 3518 7888 to Book A Service Today
Or complete the form below and one of our friendly staff will call you within 24 hours.
"Awesome service from a really excellent and friendly team."
Banksia Park, SA
To the team at Airpower.
As a small business owner myself, I think it's important to receive feedback from customers both good & bad in order to see how we are perceived in the market place. From this feedback we can make changes to improve or it can confirm we are on the right track. Unfortunately customers are quick to complain but slow, if at all to give praise and thanks for a job well done. Based on my experience in the past weeks of getting my air conditioner repaired I would like to say how impressed I am with the way your company conducted its self. The girls in admin were always very cheerful & friendly when communicating with me & at all times kept me informed as to how the job was progressing. Marty who carried out the on site work conducted himself in a very professional manner arriving on time, fit & ready for work. He was friendly & informative during his time on site & carried out his work with speed & accuracy. Congratulations all on a job well done. I would be more than happy to recommend your company to anyone seeking assistance in the service & repair of air conditioning units.
Bruce, Blewitt Springs
"As for the work done, fantastic! Very pleased with the installation. I went and had a look on the weekend and spoke to the tenants. The job was done very neatly and the tenants praised the professionalism of your staff. It was a lot different to what they said about the other AC company."
Mawson Lakes, SA
"I called to say we were absolutely thrilled with Marty's work he fixed our air conditioner and its working perfectly... It's an older unit, a Bradway and we didn't want to spend anymore money he tried a few things as the unit was only working 75% and whatever was done as a part of the service worked a treat we couldn't be happier.... Please thank him and pass on our feed back we really want him to know what a great job he's done and how very happy we are!!!"
“Excellent service from everybody in the T&K team. I would highly recommend them - they always go above and beyond!”
After contacting your office enquiring about a warranty on our air conditioners remote control yesterday morning 26/3/2018 at approx 10.30 am, we were advised of an 1800 number and the response was amazing. We recieved an sms yesterday afternoon advising us that a new remote was on its way and we recieved it in this mornings post 27/3/2018. WE RATE THIS COMPANY A 5 STAR RATING IN REGARDS TO CUSTOMER SERVICE. THANK YOU TO ALL CONCERNED.
Adelaide, South Australia
"I had 2 quotes to get my apparent unfix-able air conditioner replaced not very good timing with xmas around the corner I stumbled across TK Airpower and it ended being a simple fix saving me thousand of dollars. Lesson learnt here make sure you use qualified and experienced service repair agents."
I'm writing to thank you and T&K (especially Brett and Sam) for their efforts to restore my air conditioning. The new fan motor is now purring away, and I'm astonished to find that it is almost silent. I appreciate the comprehensive and high-quality service provided by T&K.
Rose Park, SA
“These guys fix the problems the others can't even diagnose. True professionals.”
We chose T&K Airpower as Oliver was prompt and informative in the selection of our replacement aircon system, and the installation was done professionally and works very well. On time and no hesitation to correct a small follow up issue that arose, but was quickly resolved by Marty.
Rose Park, SA